We founded in 1988, with 32 years'experience in research development and manufacture of industrial boiler. Our boiler are saled for more than 100 countries and regions like Egypt, Ethiopia, Congo, Mauritius, Tanzania,South Africa, Mexico, Ireland, Indonesia etc.
7*24 hours online service：email@example.comGet Free Quote
Product Thermal Capacity: 1 - 20 t/h
Working Pressure: 0.7 - 2 Mpa
Product Thermal Capacity: 20 - 110 t/h
Working Pressure: 1.25 - 5.3 Mpa
Product Thermal Capacity: 2 – 20t/h
Working Pressure: 1 - 2.5 MPA
Product Thermal Capacity: 4 - 35 t/h
Working Pressure: 1.0 - 2.5 MPA
May 22, 2015· Image Credit:www.globalspec.com Some common boiler problems are described below: Fires Cleanliness of the heat recovery surfaces after the boiler can often be judged by observing the gas pressure differential above and below. Any significant rise in this value should be attended to. Whilst good combustion conditions will minimise the risk, deposits allowed to accumulate in this area are a
Have you ever repaired a boiler tube leak, put the unit back into service, only to be forced offline by another leak? Identifying and correcting the root cause of tube failures is essential to help lessen the chance of future problems. A comprehensive assessment is the most effective method of determining the root cause of a failure.
Apr 30, 2019· The most common method is called the Manual J calculation. This is a room-by room heat loss calculation, and typically, a software program is used to speed up the process. The contractor starts by measuring the footprint of the home: total square feet.
A common method of level control is to use probes that sense the level of water in the boiler. At a certain level, a controller will send a signal to the feed pump to restore the water level and switching off when a predetermined level is achieved.
A qualified water treatment specialist is invaluable in determining the best method for your plant and your site specific water requirements to ensure longevity of boiler equipment and efficient operation. Number of views (9260) Comments (2) Tags: 2 comments on article "Common Boiler Problems, Part 3: Poor Water Treatment" splite. 9/15/2019 11
A boiler or steam generator is a device used to create steam by applying heat energy to water.Although the definitions are somewhat flexible, it can be said that older steam generators were commonly termed boilers and worked at low to medium pressure (7–2,000 kPa or 1–290 psi) but, at pressures above this, it is more usual to speak of a steam generator.
Mar 09, 2018· The concentration of undesirable solids in a boiler is reduced through proper feedwater treatment and the proper operation of a continuous purge (blowdown) system, and by performing intermittent blowdowns on a regular basis. The sodium zeolite water softening process is the predominant method of water treatment for boilers operating at low pressures with saturated steam. In this ion …
Boilers 291 Coagulation—a method for concentrating and removing suspended solids in boiler feedwater by adding chemicals to the water, which causes the impurities to cling together, p. 301. Condensate—condensed steam, which often is recycled back to the boiler, p. 294. Damper—a movable plate that regulates the flow of air or flue gases in boilers,
There are two methods to measure the boiler efficiency: Direct method; Indirect method; Direct method. Direct method of boiler efficiency test is more usable or more common. Boiler efficiency = power out / power in = (Q * (Hg - Hf)) / (q * GCV) * 100% Q = rate of steam flow in kg/h Hg = …
Boiler efficiency and carbon burnout. Boiler efficiency is a measure of how effectively chemical energy in fuel is converted into heat energy in steam going to the turbines. The largest boiler efficiency loss is sensible heat lost as hot flue gases (and ash) exit the boiler.
You can send a message to us by this email to firstname.lastname@example.org
If you have any problems about our product and service,please feel free to give your inquiry in the form below. We will reply you within 24 hours as soon as possible.Thank you!